Water-cooled chillers use a water-cooled condenser connected with a cooling tower.
It’s usually been used for medium and large installations that have a sufficient water supply.
Water-cooled chillers can produce a more constant performance for your application.
Water-cooled chillers range in cooling capacity from small 5-ton capacity models to several thousand-ton models for modern industries including food&beverage industries, chemical industries, manufacturing industries, breeding industries and all kinds of industrial process cooling.
Open Type Water-Cooled Chiller
Water Cooled Condenser
Water Cooling Tower
Explore Our Product Lineup
Stationary Water Cooled Chiller
Portable Water Cooled Chiller
Explosion Proof Chiller
Low Temperature Chiller
Water Cooled Scroll Chiller
Custom Water Chiller
Water-cooled Chiller Purchase Guide
Chillers, also called industrial chiller units, chilled water plants or chilled water systems, are cooling equipment that produce chilled water and are suitable for a variety of industrial and commercial applications.
SCY Chiller offers a variety of water-cooled chillers that suit a wide range of industries.
There are two different cooling media (air or water) that absorb the heat when refrigerant changes from vapor to liquid. Therefore, chillers can use two different types, air-cooled and water-cooled.
Air-cooled chillers use a condenser that is similar to the “radiators” in a car. They use a fan to force air through the refrigerant coil. Unless they are specifically designed for high ambient conditions, air-cooled condensers need to operate effectively at an ambient temperature of 35°C (95°F) or less.
Water-cooled chillers function in the same way as air-cooled chillers, but require two steps to complete the transfer of heat. First, heat enters the condenser water from the refrigerant vapor. The warm condenser water is then pumped to the cooling tower, where the heat from the process is eventually vented to the atmosphere.
When selecting water-cooled chillers for your application, it is important to ensure that the chiller has sufficient cooling capacity to handle the maximum load under the worst conditions. However, many customers fail to plan for these conditions and instead select chillers based on the nominal conditions presented in our product manuals.
Now Let’s see how to select a proper chiller with the following steps.
We can see from the above schematic, a water-cooled chiller absorbs heat from the application and transfers it to the cooling (condenser) water. The warm cooling water is then pumped to the cooling tower, and the heat generated in the process is eventually released into the atmosphere. The chilled water will be pumped to the buffer tank and stored there for subsequent use.
2. Why choose water-cooled chiller?
Consume more than 10% less energy than air-cooled chillers.
Cheaper for the same cooling capacity.
Have a longer lifespan.
Relatively quiet than air-cooled chillers.
Provide more consistent cooling performance.
Water-cooled chillers are more cost-effective than air-cooled chillers in situations where a big cooling capacity is required. (If a water-cooled chiller isn’t what you need, please refer to air-cooled chiller.)
3. How to choose the right cooling capacity for a water-cooled chiller?
One of the most frequently asked about chiller specifications is how to determine sizing/tonnage. Let’s see the below formula.
Calculate Temperature Differential = Incoming Water Temperature (°c) – Required Chilled Water Temperature
Calculate the water flow rate that you need per hour(m³/hour)
Calculate tons of cooling capacity = Water Flow Rate x Temperature Differential ÷ 0.86 ÷ 3.517
Oversize the chiller by 20% Ideal Size in Tons = Tons x 1.2
You have the ideal size for your needs.
For example, what size of chiller is required to cool 5m³ water from 25°c to 15 °c in 1 hour?
If your target temperature is lower than 5°c, please contact us for further assistance.
4. What else should I look for in choosing the right chiller?
Other important chiller specifications include the voltage required for operation, the associated pump horsepower and flow rate (contact us for custom selection), the water connection size, and the evaporator type.
Different countries and regions have different standards for industrial electricity, the common power supplies are 208-230V, 380-420V,440-480V,50Hz or 60Hz, 3phase.
4.2 Water Pump
When you decide the capacity/tonnage of the chiller, we will recommend you the suitable horsepower of the pump. Or you can check our product manual.
4.3 Connection Size
This usually depends on the water flow rate, the higher the bigger. If you want your new chiller to match your old pipes, we can also customize accordingly. For more detailed specifications, please refer to our product page or check our product manual.
R22, R410A, R407C, R404A, R134A are optional choices.
R22: good cooling effect, but R22 is considered a powerful greenhouse gas, so it’s forbidden in most countries.
R410A: eco-friendly, R-410A has replaced R-22 as the preferred refrigerant for use in residential and commercial air conditioners in Japan, Europe, and the United States. R-410A operates at higher pressures than other refrigerants.
R407C: a good replacement for R22, good cooling effect.
R404A: suitable for application that requires low temperature(below -30°c).
R134A: a non-flammable gas used primarily as a “high-temperature” refrigerant, suitable for air-cooled chiller working at a high ambient temperature.
4.5 Evaporator Choose
Air chillers have two general types of evaporators.
Shell and tube type evaporator, which requires an additional water buffer tank to use(not necessary but highly recommended).
Coil and tank evaporator, which has a built-in water storage tank for more convenient use. So there’s no need for extra buffer tanks.
These two evaporator coils can be made of 2 materials, copper or stainless steel tube.
What is the difference between these 2 options?
Copper tube: better heat transfer efficiency.
Stainless steel tube (304 or 316): also known as food-grade material, it is suitable for the food/beverage industry and can avoid water contamination.
Each unit includes hermetic scroll compressor(or semi-hermetic screw compress), water-cooled condenser, fully charged refrigerant of R22(R410A, R404A, R407C, R134A optional), shell& tube type evaporator(or tank& coil type evaporator), and a weather-resistant control center, all mounted on a beautiful and solid steel box(or rugged steel base).
At SCYChiller, we design and manufacture the best chiller units to help you overcome your most challenging problems, and SCYChiller will provide you with unconditional, expert advice to help you turn your challenges into real solutions.
To provide the best experiences, we use technologies like cookies to store and/or access device information. Consenting to these technologies will allow us to process data such as browsing behavior or unique IDs on this site. Not consenting or withdrawing consent, may adversely affect certain features and functions.
The technical storage or access is strictly necessary for the legitimate purpose of enabling the use of a specific service explicitly requested by the subscriber or user, or for the sole purpose of carrying out the transmission of a communication over an electronic communications network.
The technical storage or access is necessary for the legitimate purpose of storing preferences that are not requested by the subscriber or user.
The technical storage or access that is used exclusively for statistical purposes.The technical storage or access that is used exclusively for anonymous statistical purposes. Without a subpoena, voluntary compliance on the part of your Internet Service Provider, or additional records from a third party, information stored or retrieved for this purpose alone cannot usually be used to identify you.
The technical storage or access is required to create user profiles to send advertising, or to track the user on a website or across several websites for similar marketing purposes.